Recessed Safety Station with Recess Mounted Shower Head, Drain Pan and Daylight Drain, Fire-Rated Construction
Application: Recessed barrier-free eye/face wash and shower safety station for use in 1- and 2-hour fire-rated walls. Unit has recess mounted shower head and drain pan. Stainless steel cover provides attractive appearance and protects unit when not in use. When activated, cover serves as pan to collect waste water and return it into unit for drainage. Rather than connecting to building drainage system, unit has 1-1/2″ OD drain connection on front of unit for waste water. Front drain provides for less costly installation while facilitating regular testing of unit.
Fire Resistance: Unit can be used in 1- and 2-hour fire-rated walls without compromising integrity of wall. Unit has endothermic ceramic fiber blanket around cabinet and is sealed with fire barrier caulk. Unit is UL-listed as “Through-Penetration Firestop System No. W-L-7167.” Use fire barrier caulk when installing unit.
ADA Compliance: When installed at recommended mounting heights, unit complies with ADA requirements for accessibility by handicapped persons.
Shower Head: 11-3/4″ diameter stainless steel with flange for flush mounting in ceiling.
Shower Valve: 1″ IPS brass stay-open ball valve with stainless steel “panic bar” actuator.
Cover/Drain Pan: 16 gauge stainless steel combination cover and drain pan. Grasping “panic bar” handle and opening cover pulls spray head assembly down from vertical to horizontal position, activating water flow. While unit is in operation, waste water is collected in drain pan and returned into cabinet for drainage. Unit remains in operation until cover is returned to closed position.
Eye/Face Wash Spray Head Assembly: Two FS-Plus™ spray heads mounted on supply arms. Each spray head has individually adjustable flow control and filter to remove impurities from water.
Eye/Face Wash Valve: 1/2″ IPS brass plug-type valve with O-ring seals. Furnished with in-line strainer to protect valve from debris and foreign matter.
Mounting: 16 gauge stainless steel cabinet with flanged rim for recessed mounting in wall.
Supply: 1″ NPT female inlet.
Waste: 1 1/2″ OD tailpiece on front of unit with hinged stainless steel cover.
Sign: Furnished with ANSI-compliant identification sign.
Quality Assurance: Unit is completely assembled and water tested prior to shipment.
U.S. Patent 5,768,721
Note: ANSI Z358.1-2014 specifies that shower heads be installed no more than 96″ above the finished floor. This unit should therefore not be installed in ceilings over 8 feet. For higher ceiling heights, we recommend the SSBF2352 or SSBF2372 units.