Safety Station with Eyewash, Hand and Foot Control, All-Stainless Steel
Application: All-stainless steel combination eyewash and shower safety station. Stainless steel construction is ideal for highly corrosive environments and cleanroom applications. Eyewash is activated by flag handle or foot treadle, and features two GS-Plus™ spray-type outlet heads that deliver a flood of water for rinsing eyes.
Shower Head: 10″ diameter stainless steel with 20 GPM flow control.
Shower Valve: 1″ IPS Type 316 stainless steel stay-open ball valve. Valve has stainless steel ball and PTFE seals. Furnished with stainless steel actuating arm and 29″ stainless steel pull rod.
Spray Head Assembly: Two GS-Plus™ spray heads. Each head has a “flip top” dust cover, internal flow control and filter to remove impurities from water flow.
Eyewash Bowl: 11-1/8″ diameter stainless steel.
Eyewash Valve: 1/2″ IPS Type 316 stainless steel stay-open ball valve. Valve has stainless steel ball and PTFE seals. Eyewash is activated by flag handle or foot treadle. Unit remains in operation until handle is returned to closed position.
Pipe and Fittings: Schedule 40 Type 304 brushed stainless steel. Furnished with orange polyethylene pipe covers for high visibility and corrosion resistance.
Supply: 1-1/4″ NPT female top or side inlet.
Waste: 1-1/4″ NPT female outlet.
Sign: ANSI-compliant identification sign.
Quality Assurance: Valve and spray head assemblies are factory assembled and water tested prior to shipment.
- TM6040 Thermostatic mixing valve precisely blends hot and cold water to deliver tepid water as required by ANSI Z358.1-2014. Refer to “Thermostatic Mixing Valves” section for complete technical and product information.
- BC Stainless steel cover for eyewash bowl.
- AP275-200 Electric flashing light and alarm horn unit for mounting on wall or vertical pipe. Light illuminates and horn sounds when eyewash or shower is activated. Furnished complete with flow switch and mounting hardware.
- AP250-015 Modesty curtain for mounting on safety station.