Recessed Safety Station with Drain Pan, Exposed Shower Head
Note: Unit shown with optional AP280-235 electric light and alarm horn unit.
Application: Recessed barrier-free eye/face wash and shower safety station with ceiling mounted exposed shower head and drain pan. Stainless steel cover provides attractive appearance and protects unit when not in use. When activated, cover serves as pan to collect waste water and return it into unit for drainage.
ADA Compliance: When installed at recommended mounting heights, unit complies with ADA requirements for accessibility by handicapped persons.
Shower Head: 10″ diameter stainless steel.
Shower Valve: 1″ IPS brass stay-open ball valve with stainless steel “panic bar” actuator.
Cover/Drain Pan: 16 gauge stainless steel combination cover and drain pan. Grasping “panic bar” handle and opening cover pulls spray head assembly down from vertical to horizontal position, activating water flow. While unit is in operation, waste water is collected in drain pan and returned into cabinet for drainage. Unit remains in operation until cover is returned to closed position.
Eye/Face Wash Spray Head Assembly: Two FS-Plus™ spray heads mounted on supply arms. Each spray head has individually adjustable flow control and filter to remove impurities from water.
Eye/Face Wash Valve: 1/2″ IPS brass plug-type valve with O-ring seals. Furnished with in-line strainer to protect valve from debris and foreign matter.
Mounting: 16 gauge stainless steel cabinet with flanged rim for recessed mounting in wall. Unit fits in standard 3-5/8″ deep wall.
Pipe and Fittings: Exposed pipe and escutcheon are brushed stainless steel.
Supply: 1″ NPT female inlet.
Waste: 2″ NPT female outlet.
Sign: Furnished with ANSI-compliant identification sign.
Quality Assurance: Unit is completely assembled and water tested prior to shipment.
U.S. Patent 5,768,721
- PCC Polished chrome plated brass shower supply nipple.
- AP250-065 Modesty Curtain
- AP280-235 Electric Light and Alarm Horn
- TMV AP3800 thermostatic mixing valve.